Female Adaptor 25 × 3/4?
UK Code 7030D20
.Family Code UK 7030
.Size 25 mm × 3/4?
.Nominal Diameter (Mains) 25 mm
.Threaded Outlet Diameter 3/4?
.Standards ISO 14236, AS/NZS 4129, ISO 7/1, BS 21, DIN 2999, UNI 9561, NEN 3258, AS 1722, DIN 8076
.Design Series 7 Mechanical Compression Fittings and Valves for cold water systems, rated PN 16 (with few exceptions) and available in diameters 16mm up to 125mm. Captive o-ring seal provides life time protection against leakage and requires no nut tightening to achieve full seal. Threads, where existing, are designed to ISO 7/1 ?pipe threads where pressure tight joints are made on the threads", internal thread designation "Rp" (cylindrical) and external thread designated "R" (Tapered). We strongly recommend the use of PTFE tape in threaded connections or other appropriate sealing material.
Product Components 1 Split Ring, 1 Seal, 1 Nut
.Body Material Polypropylene, high-grade copolymer.
.Split Ring Material Polyacetal
.Nut Material Polypropylene, high-grade copolymer.
.Seal Material NBR
.Operating Temperatures Maximum temperature of use for fittings and valves is the same as that for polyethylene pipe and they are not intended for use in hot water applications. They will withstand sub-zero temperatures.
Chemical Resistance Polyacetal split rings and NBR o-rings, suitable for water, are supplied as standard. CPVC split rings and EPDM or FPM o-rings and seals are available. For aggressive chemical applications, the end user is advised to test suitability.
Description Plasson Series 7 mechanical compression fittings for Polyethylene pipe have been in continuous use since the early 60's. Many millions of such fittings are providing safe & reliable connections for water mains throughout the world. The Series 7 line consists of a large range of fitting types, sizes and patterns with many unique solutions for everyday problems. Compression fittings and valves connect PE to PE pipes. Adaptors for connecting various other pipes such as steel, copper, PVC, PP and PB are also available. These fittings are used in the municipal and rural sectors, mining, industry, agriculture and communication lines. The products are approved by major European and global agencies for use on potable water.
Excessive torque during tightening can cause nut deformation and result in joint failure; therefore use a Plasson wrench or other spanner with handle length not greater than 46 cm. If fittings are reused, avoid pull outs by ensuring the split ring is sharp and bites into the pipe. Alternatively replace split ring.
PTFE tape is strongly recommended in threaded joints.
Pressure Rating Water